This is post number 12 of a series.
Figure 6 shows a simple secondary system. The high-stage system cools the liquid R744 in the secondary circuit. The R744 is pumped around the load. It is volatile, so unlike a conventional secondary fluid such as glycol it does not remain as a liquid. Instead it partially evaporates, providing a significantly greater cooling capacity. This reduces the pump power required and the temperature difference needed at the heat exchanger.
R744 would typically be cooled to 26.6 °F (-3 °C ) for the MT load, and to -13 °F (-25 °C) for the LT load.
The high-stage system is a simple chiller-type system, typically running on an HFC, HC or Ammonia refrigerant.
In the next article of this series we’ll review the advantages and disadvantages of booster, cascade, and secondary systems. We’ll also review some case studies to determine how to select the correct system for our application.
Safety Standards Establish Usage Guidelines for A2L Refrigerants
The stage is set for the emergence of mildly flammable A2L refrigerants in U.S. commercial...
Understanding A2L Refrigerant Fundamentals — New Blog and Video Series
A2L refrigerants are a new and relatively unknown commodity in the U.S. commercial refrigeration...
New EPA Proposal Drives Regulation of HFC Phasedown in HVACR
Since the passing of the American Innovation & Manufacturing Act (AIM Act) in 2020, the HVACR...